Centrifugal fan VENTS VN 80
Centrifugal fans in plastic casing with fire-retarding damper and air capacity up to 100 m3/h.
- Capacity diagram
- Options description
|MODIFICATIONS AND OPTIONS|
|VN-A(E) 80 T— the fans are equipped with a timer.
VN-A(E) 80 TR — the fans are equipped with an adjustable timer.
|VN-A(E) 80 I — the fans are equipped with an interval switch.
VN-A(E) 80 H — the fans are equipped with a humidity sensor.
- Selection method:
- Air flow:
- Air flow: --
- Pressure: ---
Mark of conformity to the European Quality Standards and Electrical Safety issued by Association for Technical Inspection (Technischer Überwachungsverein, Germany).
CE mark means that the equipment is produced in compliance with the quality and safety standards provided by EU regulations for the given product type (marked by manufacturer).
Mark of conformity to the Ukrainian Quality Standards and electrical safety issued by UkrTEST.
Mark of conformity of the goods subject to obligatory certification in DSTR system as well as technical norms and standards acting in Russian Federation. Confirmed by the RosTEST certificates (Moscow).
|The fan is switched on to the maximum speed manually with the external switch, turn-on delay time is 50 seconds. The return to default position is performed with the timer, run-out time is 6 minutes. Continuous low speed operation is possible.|
adjustable timer modification
|The fan can be switched to the maximum speed manually with the external switch. Turn-on delay time is set with the internal regulator ranging from 0 to 150 seconds. Run-out time is set with the internal regulator from 2 to 30 minutes. Continuous low speed operation is possible.|
interval switch modification
|The fan switches periodically to the maximum speed while operation. The switching interval is set by means of the internal regulator ranging between 0.5 and 15 hours. Run-out time is 10 minutes. The fan can be switched manually with the external switch, turn-on delay time is 50 seconds. Continuous low speed operation is possible.|
humidity sensor modification
|The fan switches to the maximum speed as relative humidity level in the room increases. It switches off as relative humidity level drops by 10 % below the set level. The humidity threshold is adjusted in the range between 60 % and 90 %. Force switching to the maximum speed is provided, in this case the turn-on delay time is 50 seconds, and the run-out time is set by the internal regulator between 2 and 30 minutes. Continuous low speed operation is possible.|